Certification	EX NEPSI/ UL」
Power	3 HP(2.20Kw)3Phase
 	5 HP(3.67Kw)3Phase
2 Siphon Port	3/8 "NPT vacuum up to 635mm Hg suitable medium standard: gasoline dieselmixture of gasoline with 15% methanol or ethanol and with 20% TAME ETBEMTBE
1 Pressure Test	1/4"NPT
1 Vent	1/4"NPT
Ex-mark	ExdsII AT4 
Keep-up Pressure	0-276Kpa

Power	3HP 5HP	Outlet Pressuring Setting	160Kpa ~195Kpa
Working Voltage Range	380V/3P/50HZ	Pressure Differential	> 34Kpa
380V-415V/3P/50HZ	Dimensions	Fixed length of tubeaccording to data from user
Max. Flow Rate	600L/min (3HP) 1000L/min (5HP)	Fuel Compatibility	gasoline diesel mixture of gasoline with 15% methanol or ethanol and with 20% TAMEETBE MTBE
Protection	Motor overheating protection with motor automatic power off function	Fixed Mode	Fixed by using 6" supporting tube
Pressure Adjustable Range	0Kpa~276Kpa(Power of pipeline system when closing submersible pump)	Pipeline Leak Detection	11.4L/h(Mechanical leak detector and high flow diaphragm valve)